By Vaibhav K. Arghode, Yogendra Joshi
The short speak about essentially features of ventilation administration in raised ground info facilities. to begin with, cooling air supply via perforated tiles could be tested and impact of the tile geometry on stream box improvement and sizzling air entrainment above perforated tiles might be mentioned. Secondly, using chilly aisle containment to bodily separate cold and hot areas, and reduce cold and warm air blending might be offered. either experimental investigations and computational efforts are mentioned and improvement of computational fluid dynamics (CFD) dependent versions for simulating ventilation in facts facilities is integrated. additionally, metrology instruments for facility scale air speed and temperature dimension, and ventilation cost size via perforated ground tiles and server racks are tested and the authors current thermodynamics-based types to gauge the effectiveness and value of ventilation administration schemes in info centers.
Read Online or Download Air Flow Management in Raised Floor Data Centers PDF
Similar thermodynamics books
This e-book is the second one version of a profitable, self-contained textual content for these scholars and readers drawn to studying hypersonic circulation and high-temperature gasoline dynamics. just like the first variation, it assumes no past familiarity with both topic at the a part of the reader. when you have by no means studied hypersonic and/or high-temperature fuel dynamics sooner than, and in case you have by no means labored greatly within the sector, then this ebook is for you.
This volume offers a scientific mathematical exposition of the conceptual difficulties of nonequilibrium statistical physics, akin to entropy creation, irreversibility, and ordered phenomena. Markov chains, diffusion techniques, and hyperbolic dynamical platforms are used as mathematical versions of actual structures.
This booklet offers the basics of irreversible thermodynamics for nonlinear shipping methods in gases and beverages, in addition to for generalized hydrodynamics extending the classical hydrodynamics of Navier, Stokes, Fourier, and Fick. including its better half quantity on relativistic theories, it offers a finished photograph of the kinetic idea formulated from the perspective of nonequilibrium ensembles in either nonrelativistic and, in Vol.
- Thermodynamics and the Destruction of Resources
- Multiscale Approaches to Protein Modeling: Structure Prediction, Dynamics, Thermodynamics and Macromolecular Assemblies
- Thermodynamics of surfaces and capillary systems
- From Microphysics to Macrophysics: Methods and Applications of Statistical Physics
- The Thermodynamics of Simple Materials with Fading Memory
- Heat transfer
Additional resources for Air Flow Management in Raised Floor Data Centers
This technique has been successfully demonstrated for range of velocities from natural convection to supersonic speeds, and for micro to macro length scales. It may be noted that the air velocities encountered in a data center are generally less than 10 m/s, however, the overall length scale of the flow of interest is large (few meters). The advantage of using PIV technique, as compared to point by point velocity measurement techniques such as laser Doppler velocimetry (LDV) or hot wire anemometry, is measurement of a spatially resolved flow field at an instant of time.
For some studies requiring finer spatial resolution, another planar temperature field measurement tool was developed, see Fig. 10b. ). The construction of the tool also allows minimal physical intrusion during measurements. For a steady state experiment, the data is generally recorded for 30 s, with a sampling rate of 1 s, and the average data is reported. A time delay of 5 min is generally used for the flow field to stabilize after moving the tool to a new location. Note that this tool has also been useful in transient thermal field characterization apart from steady state experiments.
The driving potential for all three cases is the difference between the plenum (Pp) and the room pressure (Pm). We assume that Fig. 2 Air flow rate measurement analysis for passive tiles using Flow Hood. (a) Representation of air flow system in three different flow resistances. (b) Formulation of the air flow system in three different flow resistances (source: Arghode et al. 2015a). 1 Variables associated with the air flow rate measurement formulation for Flow Hood (source: Arghode et al. 2015a).